What are the start-up operations of the water ring vacuum pump?
Today we take a look at the pump operation of the water ring vacuum pump. The water ring vacuum pump is an eccentric rotor with fixed blades, which can form a variable volume rotary variable volume vacuum pump with a liquid ring.
1. Confirm that the inlet vacuum gauge of the water ring vacuum pump and the outlet pressure gauge of the steam-water separator have been installed, put into use the vacuum gauge and pressure gauge, put into use the pneumatic automatic replenishment valve and liquid level gauge of the steam-water separator, and close the bottom vent valve of the steam-water separator; Contact electrician and fitter to confirm that the steering of the motor is consistent with that of the pump and that the tools (wrench, stethoscope, rag, rag, oil pot) used are complete. Make sure that the anchor bolts of the pump are not loose, put the circulating cooling water of the cooler into use, and ensure that the return water is smooth. Slowly open the pump outlet valve, open 1/3 valve position, rotate the trolley, and then check the flange for leakage.
2. Unit water injection This pump is a closed circulation system. The supplementary water of this system is cooled by the water of the steam-water separator and then injected into the pump body again. Before opening the water ring vacuum pump, open the water injection valve of the steam-water separator and inject water into the pump body. When the three drain plugs at the bottom of the pump encounter water, screw on the drain plugs and close the water injection valve of the steam-water separator. Stop the water injection in the pump so that the water in the pump is just above the drain plug.
2. pump operation
1. Close the valve on the intake pipe, and then open the water supply gate valve. Supply water to the water ring vacuum pump. When liquid flows out of the automatic drain valve, close the inlet gate valve and turn on the motor.
2. Open the inlet gate valve.
3. When no water flows out of the automatic drain valve, start the motor and the water ring vacuum pump starts to run. At the same time, open the water supply gate valve to make the pointer of the inlet vacuum pressure gauge close to 0Mpa (gauge pressure means no vacuum). When the suction pressure of the water ring vacuum pump decreases, the pointer moves to a negative value (reading between 0 and -0.003 MPa) (vacuum is generated).
4. If the pumped gas is flammable, explosive, toxic or recyclable, the sealing liquid level of the circulating gas-water separator should be adjusted so that the liquid level is in the middle of the liquid level gauge to prevent gas leakage.
1. Confirmation and adjustment after starting: confirm that the pump flow and pressure are normal and stable, the pump vibration is normal, the external temperature of the bearing box is not more than 70 ℃, whether there is leakage, the cooling water temperature and pressure are normal, the motor current is normal, and the motor vibration sound is normal.
That's what today is all about. Therefore, it is a widely used product. At the same time, when we use this product, it is easy to ignore its pump operation, so pay attention when using it.